How to wire an AO smith replacement pool pump motor?
How to wire an AO smith replacement pool pump motor? The wiring diagram shows for a green I have an older furnace that takes an AO Smith 146A blower motor.5/5The lug on the outside isn't a ground, it's a bonding wire that is connected to the ground from the panel through the motor housing. I need to know how the wires are connected in the panel to give you the answer. If there is a 2 pole GFCI breaker and it has a red and black on it, the white should be marked green and used as a ground wire and attached to the neutral bar. The white termination on the GFCI isn't used. If the the terminations are white and black on a single pole GFCI, the wiring needs to be changed to the previous connections given. Let me know before you do anything.Correct if that is what was done in the panel. I need to know for sure to give you the correct answer. Your safety is the reason.For the installation of a 230V pump on a pool the wiring should be as follows 1) Black and Red on a 2 pole GFCI breaker to the L1 and L2 terminals on the pump. 2) an insulated ground #12 wire (should be green) from the neutral bar on main service equipment or the ground bar on a remote panel to the ground termination on the pump. 3) There isn't a need for a neutral on a 240V pump, so the wire and a connection to the GFCI breaker are omitted. It has to be exactly as instructed for your safety. If they used a wire other than green in color, it needs to be identified as a ground with green tape.He shouldn't have but should have atleast marked it. OK, connect it using the white as a ground but you should mark it. Thank you for using JustAnswer.What is the voltage the pump operates at? Check the connections at the panel for the circuit and tell me where the colors are connected and if there is any marking tape on any of them.Please open the panel and tell me how the colors are connected.
SOLVED: Wiring diagram AO Smith ST1102 pump motor - Fixya
wwwa›Forum›Pool & Spa›AO SmithWiring diagram AO Smith ST1102 pump motor - AO Smith Pool & Spa questionHi there,
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US. Here's a link to this great service Good luck!The BL6414 motor is shaded pole and does not require a capacitor.0Email me at [email protected]
and I'll reply with the from AOSmith. You need to move a couple of wires but as they say, a picture is worth me typing a thousand words.0The single lead goes to one leg, the split wired leg in the same spade goes to the other. They are usually yellow wires. As far as Hayward, Jacuzzi and Starite are concerned.0A.Oh USQ1152.0Hi, assuming you have 4-conductor wire, use the black and red wires for L1 and L2. It doesn't matter which goes to which. If you do not have a red wire, use black and white. The green or bare wire in a 3-wire cable goes to the ground. If you have 4-conductor wire, the ground wire is the one you used for the GFCI on the breaker--usually the white wire. Please let me know if you have more questions, and thanks for using FixYa.0There is almost always the wiring diagram on the outside of every spa motor. Bath Spa Parts Online0